Brand Name : HDB
Model Number : HDBAP0118H
Certification : ISO9001,CCC,ISO,ASME, GB, EN
Place of Origin : China
MOQ : 5 sets
Price : USD100,000 per set
Payment Terms : L/C, T/T, Western Union, MoneyGram
Supply Ability : 100 sets per month
Delivery Time : Within 50~70 days after receiving the down payment by T/T
Packaging Details : Iron Frame Packing for exporting with iron frame
Type : Natural Circulation
Material : Alloy steel
Usage : Power Station, heat exchanger
Color : As per customer's requirements
Condition : New
Alloy Steel Superheater And Reheater For Pulverized Coal Boilers With Natural Circulation
Description: Superheater Coil
|Material||carbon steel, alloy steel , or durable heat steel|
|Tube W.T.||0.8mm- 15mm|
In general, steam heated in high pressure superheater is named superheated vapour, the steam heated by reheater is called reheated vapour. The parameter of reheated steam is relating with economy of thermal circulation. Generally, the pressure of reheated steam is about one fifth of that of superheated steam, and the temperature of the former is almost the same as that of the latter. For example, in our nation for boiler with 125MW, 400t/h, the parmameter for superheated steam is 133.7Mpa and 555 degrees; the inlet and outlet pressure of reheated steam is 2.5/2.35MPa, their temperature is 555 degrees, too.
For boilers with 200MW, 670t/h, the parameter of superheated steam is 13.7MPa, 540 degrees; the inlet and outlet pressures are 2.7/2.5Mpa, and the temperature is also 540 degrees. For subcritical pressure control circulation boilers with 300MW, 600MW, superheated steam parameter is 18.27Mpa, 540 degrees; the inlet and outlet pressures are 3.83/3.63MPa, the temperature is also 540 dgrees. Application of steam reheating system can increase the thermal economy for power stations by 4-5%. In our country, units with capacity over 125MW all apply one time middle reheating system, and overseas, two times middle reheating systems are applied for some units with higher parameters.
Product Introduction: Superheater coil
Reheater is actually a kind of steam superheater which heats the
low-pressure steam after work and reaches a certain temperature.
The role of reheater further improves the thermal efficiency of the
circulation in power plant, and makes the steam temperature of the
last stage blade of steam turbine controlled within the allowable
A reheater is a boiler that converts steam from a steam turbine into superheated steam.
The reheater has two functions: one is to reduce the moisture of water vapor, which is beneficial to protect the turbine blade;
Second, the relative and absolute internal efficiency of steam turbine can be improved.
Details: Superheater coil
Generally 30 ~ 60 mm.The most common type of flow superheater is serpentine tube.It has a more intensive tube group, decorate in 450 ~ 1000 ℃ flue of the flue gas temperature, flue gas of vertical and lateral erosion.The flue gas mainly transfers the heat to the pipe by convection, and some of the heat is absorbed by radiation.The plate-type superheater consists of a plurality of tube screens, arranged in the upper part of the furnace or at the outlet, belonging to the radiation or semi-radiation type superheater.The former absorbs radiant heat from the furnace flame, while the latter also absorbs some convection heat.In power station boilers above 10 mpa, both screen type and serpentine type superheater are commonly used to increase heat absorption.The wall superheater applied on the inner wall of the furnace is radiant superheater, which is seldom used.The wall-mounted superheater is used in the large capacity power station boiler to form the wall of the furnace top and convection flue.The picture shows the arrangement of several superheater.The small capacity industrial boilers with superheater can meet the requirements only with single stage superheater.
The reheater layout follows the superheater layout, including convection, radiation and semi-radiation.
The convection reheater has reverse flow, downstream flow and mixed flow, single coil, double coil, multi-coil, parallel and staggered, vertical and horizontal type, parallel to the front wall and perpendicular to the front wall.Convection reheater is the main reheater that absorbs convection heat.
Radiant reheater refers to the reheater absorbing furnace radiation.
Semi-radiant reheaters (plate superheater) refer to reheaters that absorb more radiation from the furnace (more than 1/2 of the total heat).
The material selection principle of reheater is the same as that of superheater. Since reheating steam is inferior to superheater in cooling capacity, the design wall temperature is generally higher than that of superheater of the same temperature level.Metal tubes of high temperature reheaters are generally made of alloy steel (metal tubes containing more than 5% of alloy elements).For example, 12CrlMoV, steel 102, sa213-t91, sa213-tp304, sa213-tp347, etc.
Hua Dong Boiler has become a major qualified supplier of domestic and foreign boiler manufacturers and energy companies, including American Covanta Energy Company, AMEC Foster Wheeler Company, ALSTOM, Oriental Boiler Limited by Share Ltd., Harbin electric LLC, Wuxi Hua Guang Boiler Co., Ltd., Hangzhou Boiler Group Co., Ltd.
Alloy Steel Pulverized Superheater Coil Tube With Natural Circulation Images